Main Low Tension Switchboard:
Fully Type Tested till 6000 Amps till 100KA as per IEC 61439, and Internal ARC Tested for the same current rating as per IEC 61641. Type Tested for a Bus-Coupler Specimen as per actual Project Conditions with Temperature Rise Test done for an average ambient of 50 Deg Celcius to a maximum ambient of 55 Degree Celcius.GCG MLTPs Type Tested for various IP Rating combinations of IP43, IP54 & IP55 in addition to Form of Construction Combinations of Form3b & 4b. GCG MLTPs Type Tested for Fault Levels of 65KA, 80KA & 100KA and also have achieved the unique feature of having passed a 3 second Type Test of 55KA, 3 Second on a 3000 Amps Specimen, which is equivalent to 95KA, 1second.
Cellular Switch Board:
Fully Type tested till 1400 Amps, for a Fault Level of 50KA as per IEC 61439, Form 4b Type of Construction and IP54 Degree of Protection for an average ambient of 50 degrees.
Drawout Motor Control Centres:
Fully Type tested till 1600 Amps, for a Fault Level of 50KA as per IEC 61439, Form 4b Type of Construction and IP54 Degree of Protection for an average ambient of 50 degrees.
Main Switch Board:
Fully Type tested till 500 Amps, for a Fault Level of 40KA as per IEC 61439 for a Cubicle Construction, Type Form 2.
Fully Type Tested till 125 Amps for IEC MCBs.
MEW Feeder Pillars:
Approved Manufacturers for MEW Street Lighting Feeder Pillars of Type-A, Type-B & Type-C Technical Specifications.
Other Product Line includes:
|Generator Totalizing Panels upto 12,000 Amps|
|Generator Synchronizing Panels|
|VFD Motor Control Panels upto 560 KW|
|11KV Pump Control Panels|
|Soft Starter Motor Control Panels upto 450KW|
|DOL, 2 Speed & Star Delta Motor Control Panels|